WQ Submersible Sewage Pumps
WQ2000 -20 -one hundred sixty
WQ — submersible sewage pump
2000 — circulation capacity (m3/h)
20 — head(m)
one hundred sixty — electrical power p2 (kw)
WQ collection submersible sewage pump has trustworthy performance and best good quality. It can be used broadly. This collection pump adopts some know-how technology, its construction which can resist tear and clog can guarantee successfully that the solid particle (φ 50mm- 125mm) and fiber such as cotton, weed can move effortlessly.
WQ series pump can be utilized on numerous software this kind of as mine, municipal engineering, healthcare facility, hotel, village and marsh gasoline tank to pump civil sewage and industrical pollution h2o. It is also utilized to oil extraction and irrigation. Running variety:
1. CZPT temperature: forty °
2. pH: five-nine.
Spend attention to set up:
Just before working pump, a certified electrician ought to examine pump method. Be sure to make some electrical products defense steps as adhere to:
one. Before working pump, a -500V megohmmeter should be utilised to measure resistance of the motor to the ground. Minimum resistance is 1 megohm.
two. Electricity voltage deviation can not exceed ± 10% of the rated voltage which is confirmed on the nameplate.
3. Check the motor rotation. Before running the pump, begin the pump on the ground, check the rotation is the very same with the rotation marked on the pump entire body. If not, adjust two of them.
4. The pump should be managed by a special panel. As pump with many protection device, like leakage keep track of, temperature sensor, and so on. These device can protect pump from injury and lengthen the pump lifestyle.
CZPT attribute (appear table)
Set up size
If you need any type, pls get in touch with us
We aslo could redesign it for customer’s prerequisite
You could refer to our site. http://en.lanshengroup.com